A) Securely attach the hanger to the building structure
at a point where the load coupling is directly over the desired point
B Make certain that the moving parts of the hanger will be unobstructed.
C) Make certain that the rod has enough thread engagement before taking
up the load.
D) Turn the load coupling until the travel stop is free.
E) Prior to the final start-up please remove the travel stop.
F) After the line is in operation, check the hanger for indicated hot
position. If necessary, make adjustment by turning the load coupling to
bring the indicator to the hot position. No other adjustment is normally
required since the load as calibrated at the factory is equal to the load
specified to be supported.